The studies conducted by the utility were helpful in that they provided data for discovering the most predominant source of the sags and for determining the most reliable alternative circuit to feed Plant 1.
The best solutions were achieved jointly by the utility and customer working together. The solution of moving the operations of Plant 2 to a new location and building a new circuit was more expensive than the utility would have typically suggested.
These solutions have been implemented. The utility has not heard from this customer since these changes were made.
This white paper includes: